// CODE SNIPPET
1910.305(g)(2) Identification, Splices, and Terminations
JUMP TO FULL CODE CHAPTER
A conductor of a flexible cord or cable that is used as a grounded conductor or an equipment grounding conductor shall be distinguishable from other conductors. Types S, SC, SCE, SCT, SE, SEO, SEOO, SJ, SJE, SJEO, SJEOO, SJO, SJT, SJTO, SJTOO, SO, SOO, ST, STO, and STOO flexible cords and Types G, G-GC, PPE, and W flexible cables shall be durably marked on the surface at intervals not exceeding 610 mm (24 in.) with the type designation, size, and number of conductors.
Flexible cords and cables shall be connected to devices and fittings so that strain relief is provided that will prevent pull from being directly transmitted to joints or terminal screws.
Flexible cords may be used only in continuous lengths without splice or tap. Hard-service cord and junior hard-service cord No. 14 and larger may be repaired if spliced so that the splice retains the insulation, outer sheath properties, and usage characteristics of the cord being spliced.
Related Code Sections
1910.305(g)(2) Electrical, Identification, Splices, and Terminations
or terminal screws. Flexible cords may be used only ...
OSHA 1910 General Industry > S Electrical > 1910.305 Wiring Methods, Components, and Equipment for General Use > 1910.305(g) Flexible Cords and Cables > 1910.305(g)(2) Identification, Splices, and Terminations
1910.302(b)(1) Electrical, Requirements Applicable to All Installations
§ 1910.305(g)(2)(ii) and (g)(2)(iii) -- Flexible cords and cables -- Identification, splices, and terminations § 1910.307, except as specified ...
OSHA 1910 General Industry > S Electrical > 1910.302 Electric Utilization Systems > 1910.302(b) Extent of Application > 1910.302(b)(1) Requirements Applicable to All Installations
1910.308(d)(4) Electrical, Identification
Fire alarm circuits shall be identified at terminal and junction locations in a manner that will prevent unintentional interference ...
OSHA 1910 General Industry > S Electrical > 1910.308 Special Systems > 1910.308(d) Fire Alarm Systems > 1910.308(d)(4) Identification
1910.303(c)(2) Electrical, Terminals
Connection of conductors to terminal parts shall ensure a good connection without damaging the conductors and shall be made by means of pressure ...
OSHA 1910 General Industry > S Electrical > 1910.303 General > 1910.303(c) Electrical Connections > 1910.303(c)(2) Terminals
1910.184(h)(3) Materials Handling and Storage, Splicing
Spliced fiber rope slings shall not be used unless they have been spliced in accordance with the following minimum requirements and in accordance ...
OSHA 1910 General Industry > N Materials Handling and Storage > 1910.184 Slings > 1910.184(h) Natural and Synthetic Fiber-Rope Slings > 1910.184(h)(3) Splicing