1224.39.5 Hyperbaric Therapy Service Space
- Clearances. There shall be a minimum clearance of 3 feet (914 mm) around the chamber. The area in front of the chamber entry designed for gurney or bed access shall have a minimum clearance of 8 feet (2438 mm) for gurney or bed approach. The area in front of the chamber entry designed for ambulatory or wheelchair access only shall have a minimum clearance of 5 feet (1524 mm) for wheelchair approach.
- Entries. Chamber entries shall be provided with access ramps that are flush with the chamber entry doorway. Chamber entries not designed for gurney/bed access shall be a minimum of 3 feet (914 mm).
- Clearances. There shall be a minimum clearance of 3 feet (914 mm) around the chamber. A minimum clearance of 44 inches (1118 mm) shall be provided between the control sides of two chambers. The area in front of the chamber entry shall be designed for gurney or bed access with a minimum clearance of 8 feet (2438 mm) for gurney or bed approach.
- Oxygen. An oxygen service valve shall be provided for each chamber.
In facilities with a Class A hyperbaric chamber or with three or more Class B chambers, a pre-procedure/ patient holding area shall be provided to accommodate patients on gurneys or beds and sitting space for ambulatory patients. The area shall permit visual observation of the patient by nursing staff and be located out of traffic flow. Each gurney station shall be a minimum clear floor area of 80 square feet (7.43 m2) and shall have a minimum clearance of 3 feet (914 mm) on the sides of the gurneys and the foot of the gurney. There shall be provisions for privacy such as cubicle curtains.
Refer to Table 1126.96.36.199 Station Outlets for Oxygen, Vacuum (Suction) and Medical Air.
An administrative center/nurse station shall be provided within the hyperbaric suite.
Room(s) for individual consultation and treatment shall be provided and meet the requirements of Section 1188.8.131.52.
A clean linen storage area shall be provided. This may be within the clean utility room, a separate closet or an approved distribution system. If a closed cart system is used, storage may be in an alcove. It must be out of the path of normal traffic and under staff control.
A clean supply room shall be provided and meet the requirements of Section 1184.108.40.206.1. This room may be omitted if the suite is served by a cart system.
The gas cylinder room shall provide space to house eight (H) cylinders and two gas manifolds, consisting of at least two (H) cylinders on each manifold.
A housekeeping room shall be provided and shall be immediately accessible to the hyperbaric suite.
A compressor room shall be provided to house the chamber compressors, accumulator tanks and fire suppression system.
Toilet rooms with a handwashing stations shall be immediately accessible to the hyperbaric suite for staff use.
The patient waiting area shall be provided and meet the requirements of Section 1224.39.1.
Changing area(s) for outpatients shall be provided for patient clothing and for securing valuables.
A patient toilet room with a handwashing station shall be directly accessible to the hyperbaric suite.