// CODE SNIPPET
P-811.1.1 How Measured
Related Code Sections
P-811.1.1 Water Supply and Distribution, How Measured
The residual pressure shall be measured at the pressure side of the water outlet with the outlet fully open ...
Philadelphia Plumbing Code > 8 Water Supply and Distribution > P-811 Water Supply Fixtures > P-811.1 Minimum Pressure > P-811.1.1 How Measured
1803.5.12 Soils and Foundations, Seismic Design Categories D Through F
systems to accommodate anticipated displacements and forces. 4.3. Ground stabilization. 4.4. Any combination of these measures and how they shall ...
2018 Philadelphia Building Code > 18 Soils and Foundations > 1803 Geotechnical Investigations > 1803.5 Investigated Conditions > 1803.5.12 Seismic Design Categories D Through F
C408.3.2 [CE] Commercial Energy Efficiency, Documentation Requirements
the following: Name and address of not less than one service agency for installed equipment. A narrative of how each system is intended to operate, including ...
2018 Philadelphia Energy Conservation Code > 4 [CE] Commercial Energy Efficiency > C408 Maintenance Information and System Commissioning > C408.3 Functional Testing of Lighting Controls > C408.3.2 Documentation Requirements
404.2.3.1 Emergency Planning and Preparedness, Lockdown Plan Contents
Lockdown plans shall include the following: Identification of individuals authorized to issue a lockdown order. Security measures used during ...
2018 Philadelphia Fire Code > 4 Emergency Planning and Preparedness > 404 Fire Safety, Evacuation and Lockdown Plans > 404.2 Contents > 404.2.3 Lockdown Plans > 404.2.3.1 Lockdown Plan Contents