// CODE SNIPPET
JUMP TO FULL CODE CHAPTER
The employer shall assure that every 1 1/2 inch (3.8 cm) or smaller hose outlet used to meet this standard is equipped with hose connected and ready for use. In extremely cold climates where such installation may result in damaged equipment, the hose may be stored in another location provided it is readily available and can be connected when needed.
Standpipe systems installed after January 1, 1981, for use by employees, shall be equipped with lined hose. Unlined hose may remain in use on existing systems. However, after the effective date of this standard, unlined hose which becomes unserviceable shall be replaced with lined hose.
Related Code Sections
1910.158(c)(3) Fire Protection, Hose
The employer shall assure that every 1 1 / 2 inch (3.8 cm) or smaller hose outlet used to meet this standard is equipped with hose connected ...
OSHA 1910 General Industry > L Fire Protection > 1910.158 Standpipe and Hose Systems > 1910.158(c) Equipment > 1910.158(c)(3) Hose
1910.253(e)(5) Welding, Cutting, and Brazing, Hose and Hose Connections
Hose for oxy-fuel gas service shall comply with the Specification for Rubber Welding Hose, 1958, Compressed Gas Association and Rubber Manufacturers ...
OSHA 1910 General Industry > Q Welding, Cutting, and Brazing > 1910.253 Oxygen-Fuel Gas Welding and Cutting > 1910.253(e) Protective Equipment, Hose, and Regulators > 1910.253(e)(5) Hose and Hose Connections
1910.106(f)(4)(vii) Hazardous Materials, Hoses and Couplings
All pressure hoses and couplings shall be inspected at intervals appropriate to the service. The hose and couplings shall be tested with the hose ...
OSHA 1910 General Industry > H Hazardous Materials > 1910.106 Flammable Liquids > 1910.106(f) Bulk Plants > 1910.106(f)(4) Wharves > 1910.106(f)(4)(vii) Hoses and Couplings
1910.107(e)(6) Hazardous Materials, Pipes and Hoses
All containers or piping to which is attached a hose or flexible connection shall be provided with a shutoff valve at the connection. Such valves ...
OSHA 1910 General Industry > H Hazardous Materials > 1910.107 Spray Finishing Using Flammable and Combustible Materials > 1910.107(e) Flammable Liquids and Liquids With a Flashpoint Greater Than 199.4 °F (93 °C) > 1910.107(e)(6) Pipes and Hoses
1910.109(a)(12) Hazardous Materials, Semiconductive Hose
Semiconductive hose - a hose with an electrical resistance high enough to limit flow of stray electric currents to safe levels, yet not so high ...
OSHA 1910 General Industry > H Hazardous Materials > 1910.109 Explosives and Blasting Agents > 1910.109(a) Definitions Applicable to This Section > 1910.109(a)(12) Semiconductive Hose