// CODE SNIPPET
904.8.2 High-Pressure Cylinders
Related Code Sections
904.8.2 Fire Protection and Life Safety Systems, High-Pressure Cylinders
High-pressure cylinders shall be weighed and the date of the last hydrostatic test shall be verified at six-month intervals. Where a container shows ...
Fire Code 2018 of Kansas > 9 Fire Protection and Life Safety Systems > 904 Alternative Automatic Fire-Extinguishing Systems > 904.8 Carbon Dioxide Systems > 904.8.2 High-Pressure Cylinders
3509.5 Welding and Other Hot Work, Identification of Manifolds
-PRESSURE MANIFOLD DO NOT CONNECT HIGH-PRESSURE CYLINDERS MAXIMUM PRESSURE 250 PSIG ...
Fire Code 2018 of Kansas > 35 Welding and Other Hot Work > 3509 Piping Manifolds and Hose Systems for Fuel Gases and Oxygen > 3509.5 Identification of Manifolds
3.18.3 Hydraulic Elevators, Cylinders
For pressure calculations, the cylinder and connecting coupling shall have a factor of safety ...
Safety Code for Elevators and Escalators 2016 of Kansas > 3 Hydraulic Elevators > 3.18 Hydraulic Jacks > 3.18.3 Cylinders
413.9.1 Gas Piping Installations, Closed Transfer System
The procedure shall include what actions the operator will take in the event of a low-pressure or high-pressure natural gas release during ...
Fuel Gas Code 2018 of Kansas > 4 Gas Piping Installations > 413 (IFGC) Compressed Natural Gas Motor Vehicle Fuel-Dispensing Facilities > 413.9 Discharge of CNG From Motor Vehicle Fuel Storage Containers > 413.9.1 Closed Transfer System
2308.8.1.1 Motor Fuel-Dispensing Facilities and Repair Garages, Closed Transfer System
and approval. The procedure shall include what actions the operator will take in the event of a low-pressure or high-pressure natural gas release during ...
Fire Code 2018 of Kansas > 23 Motor Fuel-Dispensing Facilities and Repair Garages > 2308 Compressed Natural Gas Motor Fuel-Dispensing Facilities > 2308.8 Discharge of CNG From Motor Vehicle Fuel Storage Containers > 2308.8.1 Methods of Discharge > 2308.8.1.1 Closed Transfer System