// CODE SNIPPET
110.15 High-Leg Marking
JUMP TO FULL CODE CHAPTER
On a 4-wire, delta-connected system where the midpoint of one phase winding is grounded, only the conductor or busbar having the higher phase voltage to ground shall be durably and permanently marked by an outer finish that is orange in color or by other effective means. Such identification shall be placed at each point on the system where a connection is made if the grounded conductor is also present.
Related Code Sections
110.15 General, High-Leg Marking
to ground shall be durably and permanently marked by an outer finish that is orange in color or by other effective means. Such identification shall ...
National Electrical Code 2020 of Minnesota > 1 General > 110 Requirements for Electrical Installations > 110.15 High-Leg Marking
(1) Equipment for General Use, High-Leg Identification
be legibly and permanently field marked as follows: "Caution _____ Phase Has _____ Volts to Ground" ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 408 Switchboards, Switchgear, and Panelboards > 408.3 Support and Arrangement of Busbars and Conductors > (F) Switchboard, Switchgear, or Panelboard Identification > (1) High-Leg Identification
3.3.138 Definitions, Leg Facility
The portion of a communications channel that connects not more than one protected premises to a primary or secondary trunk facility. The leg facility ...
National Fire Alarm and Signaling Code 2016 of Minnesota > 3 Definitions > 3.3 General Definitions > 3.3.138 Leg Facility
353.120 Wiring Methods and Materials, Marking
Each length of HDPE shall be clearly and durably marked at least every 3 m (10 ft) as required in 110.21. The type of material shall also be included ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 353 High Density Polyethylene Conduit: Type HDPE Conduit > 353.120 Marking
410.146 Equipment for General Use, Marking
Each luminaire or each secondary circuit of tubing having an open-circuit voltage of over 1000 volts shall have a clearly legible marking in letters ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 410 Luminaires, Lampholders, and Lamps > 410.146 Marking