The minimum unobstructed total area of the outside and return air
ducts or openings to a heat pump
shall be not less than 6 square inches per 1,000 Btu/h
(13 208 mm2
/kW) output rating or as indicated by the conditions of the listing of the heat pump
. Electric heat pumps
shall conform to UL 1995.