// CODE SNIPPET
Section P-511 Hair and Lint Interceptors
JUMP TO FULL CODE CHAPTER
An approved hair or lint interceptor shall be installed wherever hair or lint is introduced into the drainage system in sufficient quantity to cause line stoppage and shall be installed in connection with the following uses or occupancies when required by the Industrial Waste Division of the Water Department.
- Commercial, institutional, hotel, club or other laundries equipped with commercial-type laundry equipment;
- Beauty parlors and beauty operator training schools having 6 or more lavatories draining to a common house drain;
- Dry cleaning establishments;
- Hide or fur processing plants;
- Establishments having laundry equipment on the premises for public use.
Related Code Sections
Section P-511 Traps, Cleanouts, Interceptors, and Backwater Valves, Hair and Lint Interceptors
An approved hair or lint interceptor shall be installed wherever hair or lint is introduced into the drainage system in sufficient quantity to cause ...
Philadelphia Plumbing Code > 5 Traps, Cleanouts, Interceptors, and Backwater Valves > P-511 Hair and Lint Interceptors
2188.8.131.52 Dry Cleaning, Lint
Lint and refuse shall be removed from traps daily, deposited in approved waste cans, removed from the premises, and disposed of safely. At all ...
2018 Philadelphia Fire Code > 21 Dry Cleaning > 2105 Operating Requirements > 2105.1 General > 2105.1.5 Equipment Maintenance and Housekeeping > 2184.108.40.206 Lint
Section 1003 Traps, Interceptors and Separators, Interceptors and Separators
Interceptors and separators shall be provided to prevent the discharge of oil, grease, sand and other substances harmful or hazardous to the public ...
Plumbing Code 2018 of Philadelphia > 10 Traps, Interceptors and Separators > 1003 Interceptors and Separators
1009.3 Change of Occupancy, Interceptor Required
If the new occupancy will produce grease or oil-laden wastes, interceptors shall be provided as required in the International Plumbing Code ...
2018 Philadelphia Existing Building Code > 10 Change of Occupancy > 1009 Plumbing > 1009.3 Interceptor Required
506.3 Plumbing Facilities and Fixture Requirements, Grease Interceptors
Where it has been determined that a grease interceptor is not being maintained and serviced as intended by this code and the manufacturer's ...
Philadelphia Property Maintenance Code > 5 Plumbing Facilities and Fixture Requirements > 506 Sanitary Drainage System > 506.3 Grease Interceptors