Single-or multiple-station smoke alarms shall be installed in all of the following locations in Group R-1 and "SRO" occupancies:
- In sleeping areas.
- In every room in the path of the means of egress from the sleeping area to the door leading from the sleeping unit.
- In each story within the sleeping unit, including basements. For sleeping units with split levels and without an intervening door between the adjacent levels, a smoke alarm installed on the upper level shall suffice for the adjacent lower level provided that the lower level is less than one full story below the upper level.