// CODE SNIPPET
[F] 907.2.6.3 Group I-3 Occupancies
JUMP TO FULL CODE CHAPTER
An automatic smoke detection system shall be installed throughout resident housing areas, including sleeping units and contiguous day rooms, group activity spaces and other common spaces normally accessible to residents.
- Other approved smoke detection arrangements providing equivalent protection, including, but not limited to, placing detectors in exhaust ducts from cells or behind protective guards listed for the purpose, are allowed when necessary to prevent damage or tampering.
- Sleeping units in Use Conditions 2 and 3 as described in Section 308.
- Smoke detectors are not required in sleeping units with four or fewer occupants in smoke compartments that are equipped throughout with an automatic sprinkler system installed in accordance with Section 903.3.1.1.
Related Code Sections
2702.2.17 Electrical, Group I-3 Occupancies
Emergency power shall be provided for doors in Group I-3 occupancies in accordance with Section 408.4.2 ...
Ohio Building Code 2011 > 27 Electrical > 2702 Emergency and Standby Power Systems > 2702.2 Where Required > 2702.2.17 Group I-3 Occupancies
2702.2.7 Electrical, Group I-3 Occupancies
Emergency power shall be provided for power-operated doors and locks in Group I-3 occupancies as required in Section 408.4.2 ...
Ohio Building Code 2017 > 27 Electrical > 2702 Emergency and Standby Power Systems > 2702.2 Where Required > 2702.2.7 Group I-3 Occupancies
408.7 Ohio Administrative Code 1301:7-7-04 Emergency Planning and Preparedness, Group I-3 Occupancies
Group I-3 occupancies shall comply with the requirements of paragraphs (H)(7)(a)(408.7.1) to (H)(7)(d)(408.7.4) of this rule and paragraphs ...
Ohio Fire Code 2011 > Ohio Administrative Code 1301:7-7-04 Emergency Planning and Preparedness > 408 Use and Occupancy-Related Requirements > 408.7 Group I-3 Occupancies
604.2.16 Ohio Administrative Code 1301:7-7-06 Building Services and Systems, Group I-3 Occupancies
Power-operated sliding doors or power-operated locks for swinging doors in Group I-3 occupancies shall be operable by a manual release mechanism ...
Ohio Fire Code 2011 > Ohio Administrative Code 1301:7-7-06 Building Services and Systems > 604 Emergency and Standby Power Systems > 604.2 Where Required > 604.2.16 Group I-3 Occupancies
907.2.6.3 Ohio Administrative Code 1301:7-7-09 Fire Protection Systems, Group I-3 Occupancies
Group I-3 occupancies shall be equipped with a manual fire alarm system and automatic smoke detection system installed for alerting staff ...
Ohio Fire Code 2011 > Ohio Administrative Code 1301:7-7-09 Fire Protection Systems > 907 Fire Alarm and Detection Systems > 907.2 Where Required-New Buildings and Structures > 907.2.6 Group I > 907.2.6.3 Group I-3 Occupancies