// CODE SNIPPET
[F] 907.2.6.3 Group I-3 Occupancies
JUMP TO FULL CODE CHAPTER
An automatic smoke detection system shall be installed throughout resident housing areas, including sleeping units and contiguous day rooms, group activity spaces and other common spaces normally open to residents.
- Other approved smoke detection arrangements providing equivalent protection, including, but not limited to, placing detectors in exhaust ducts from cells or behind protective guards listed for the purpose, are allowed where necessary to prevent damage or tampering.
- Sleeping units in Use Conditions 2 and 3 as described in Section 308.
- Smoke detectors are not required in sleeping units with four or fewer occupants in smoke compartments that are equipped throughout with an automatic sprinkler system installed in accordance with Section 903.3.1.1.
Related Code Sections
2702.2.9 Electrical, Group I-3 Occupancies
Emergency power shall be provided for power-operated doors and locks in Group I-3 occupancies as required in Section 408.4.2 ...
Building Code 2018 of Illinois > 27 Electrical > 2702 Emergency and Standby Power Systems > 2702.2 Where Required > 2702.2.9 Group I-3 Occupancies
907.2.6.3 Fire Protection and Life Safety Systems, Group I-3 Occupancies
Group I-3 occupancies shall be equipped with a manual fire alarm system and automatic smoke detection system installed for alerting staff ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 907 Fire Alarm and Detection Systems > 907.2 Where Required—New Buildings and Structures > 907.2.6 Group I > 907.2.6.3 Group I-3 Occupancies
712.1.14 Fire and Smoke Protection Features, Group I-3
In Group I-3 occupancies, vertical openings shall be permitted in accordance with Section 408.5 ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 712 Vertical Openings > 712.1 General > 712.1.14 Group I-3
803.4.1.4 Alterations—Level 2, Group I-3
A fire alarm system shall be installed in work areas of Group I-3 occupancies as required by the International Fire Code ...
Existing Building Code 2018 of Illinois > 8 Alterations—Level 2 > 803 Fire Protection > 803.4 Fire Alarm and Detection > 803.4.1 Occupancy Requirements > 803.4.1.4 Group I-3
805.10.1.2 Alterations—Level 2, Group I-3
In Group I-3 occupancies, the required capacity of the refuge areas for smoke compartments in accordance with Section 408.6.2 of the International ...
Existing Building Code 2018 of Illinois > 8 Alterations—Level 2 > 805 Means of Egress > 805.10 Refuge Areas > 805.10.1 Capacity > 805.10.1.2 Group I-3