// CODE SNIPPET
406.1.4 Group I-2 Receptacles
JUMP TO FULL CODE CHAPTER
Receptacles in patient bed locations of Group I-2 that are not "hospital grade" shall be replaced with "hospital grade" receptacles, as required by NFPA 99 and Article 517 of NFPA 70.
Related Code Sections
406.1.4 Repairs, Group I-2 Receptacles
Receptacles in patient bed locations of Group I-2 that are not "hospital grade" shall be replaced with "hospital grade" receptacles, as required ...
Existing Building Code 2018 of Illinois > 4 Repairs > 406 Electrical > 406.1 Material > 406.1.4 Group I-2 Receptacles
Section 807 Alterations—Level 2, Electrical
wiring in all work areas in Group A-1, A-2, A-5, H and I occupancies shall be upgraded to meet the materials and methods requirements of Chapter 7 ...
907.2.6 Fire Protection and Life Safety Systems, Group I
with Sections 907.2.6.1, 907.2.6.2 and 907.2.6.3.3. Exceptions: Manual fire alarm boxes in sleeping units of Group I-1 and I-2 occupancies ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 907 Fire Alarm and Detection Systems > 907.2 Where Required—New Buildings and Structures > 907.2.6 Group I
1107.5 Accessibility, Group I
be Accessible units . In Group I-1, Condition 2, at least 10 percent, but not less than one, of the dwelling units and sleeping units shall be Accessible ...
Building Code 2018 of Illinois > 11 Accessibility > 1107 Dwelling Units and Sleeping Units > 1107.5 Group I
1008.2.2 Means of Egress, Group I-2
In Group I-2 occupancies where two or more exits are required, on the exterior landings required by Section 1010.1.6, means of egress illumination ...
Building Code 2018 of Illinois > 10 Means of Egress > 1008 Means of Egress Illumination > 1008.2 Illumination Required > 1008.2.2 Group I-2