// CODE SNIPPET
[F] 907.2.6.1 Group I-1
JUMP TO FULL CODE CHAPTER
In Group I-1 occupancies, an automatic smoke detection system shall be installed in corridors, waiting areas open to corridors and habitable spaces other than sleeping units and kitchens. The system shall be activated in accordance with Section 907.5.
Related Code Sections
1107.5.1 Accessibility, Group I-1
Accessible units and Type B units shall be provided in Group I-1 occupancies in accordance with Sections 1220.127.116.11 and 118.104.22.168 ...
Building Code 2018 of Illinois > 11 Accessibility > 1107 Dwelling Units and Sleeping Units > 1107.5 Group I > 1107.5.1 Group I-1
803.4.1.2 Alterations—Level 2, Group I-1
A fire alarm system shall be installed in work areas of Group I-1 residential care/assisted living facilities as required by the International ...
Existing Building Code 2018 of Illinois > 8 Alterations—Level 2 > 803 Fire Protection > 803.4 Fire Alarm and Detection > 803.4.1 Occupancy Requirements > 803.4.1.2 Group I-1
907.2.6.1 Fire Protection and Life Safety Systems, Group I-1
In Group I-1 occupancies, an automatic smoke detection system shall be installed in corridors, waiting areas open to corridors and habitable ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 907 Fire Alarm and Detection Systems > 907.2 Where Required—New Buildings and Structures > 907.2.6 Group I > 907.2.6.1 Group I-1
308.2 Occupancy Classification and Use, Institutional Group I-1
Institutional Group I-1 occupancy shall include buildings, structures or portions thereof for more than 16 persons, excluding staff, who reside ...
Building Code 2018 of Illinois > 3 Occupancy Classification and Use > 308 Institutional Group I > 308.2 Institutional Group I-1
420.8 Special Detailed Requirements Based on Occupancy and Use, Group I-1 Cooking Facilities
In Group I-1 occupancies, rooms or spaces that contain cooking facilities with domestic cooking appliances shall be in accordance with all ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 420 Groups I-1, R-1, R-2, R-3 and R-4 > 420.8 Group I-1 Cooking Facilities