[F] 415.5.1 Group H Occupancy Minimum Fire Separation Distance
Regardless of any other provisions, buildings containing Group H occupancies shall be set back to the minimum fire separation distance as set forth in Sections 4220.127.116.11 through 418.104.22.168. Distances shall be measured from the walls enclosing the occupancy to lot lines, including those on a public way. Distances to assumed lot lines established for the purpose of determining exterior wall and opening protection are not to be used to establish the minimum fire separation distance for buildings on sites where explosives are manufactured or used when separation is provided in accordance with the quantity distance tables specified for explosive materials in the Florida Fire Prevention Code.
Group H-1 occupancies shall be set back not less than 75 feet (22 860 mm) and not less than required by the Florida Fire Prevention Code.
Group H-2 occupancies shall be set back not less than 30 feet (9144 mm) where the area of the occupancy is greater than 1,000 square feet (93 m2) and it is not required to be located in a detached building.