// CODE SNIPPET
(A) Grounding Type
JUMP TO FULL CODE CHAPTER
Except as provided in 406.4(D), receptacles installed on 15- and 20-ampere branch circuits shall be of the grounding type. Grounding-type receptacles shall be installed only on circuits of the voltage class and current for which they are rated, except as provided in 210.21(B)(1) for single receptacles or Table 210.21(B)(2) and Table 210.21(B)(3) for two or more receptacles.
Related Code Sections
(A) Equipment for General Use, Grounding Type
Except as provided in 406.4(D), receptacles installed on 15- and 20-ampere branch circuits shall be of the grounding type. Grounding-type receptacles ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 406 Receptacles, Cord Connectors, and Attachment Plugs (Caps) > 406.4 General Installation Requirements > (A) Grounding Type
(A) Special Occupancies, Grounding-Type Receptacle Outlets
All receptacle outlets shall comply with the following: Be of grounding type Be installed according to 406.4 Except where supplying specific ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 550 Mobile Homes, Manufactured Homes, and Mobile Home Parks > 550.13 Receptacle Outlets > (A) Grounding-Type Receptacle Outlets