// CODE SNIPPET
E3603.1.4 Grounded Conductors
Related Code Sections
E3407.1 General Requirements, Grounded Conductors
Insulated grounded conductors of sizes 6 AWG or smaller shall be identified by a continuous white or gray outer finish or by three continuous white ...
Residential Code 2015 of Utah > 34 General Requirements > E3407 Conductor and Terminal Identification > E3407.1 Grounded Conductors
E3603.1.4 Services, Grounded Conductors
The grounded conductor ampacity shall be not less than the maximum unbalance of the load and the size of the grounded conductor shall be not smaller ...
Residential Code 2015 of Utah > 36 Services > E3603 Service, Feeder and Grounding Electrode Conductor Sizing > E3603.1 Grounded and Ungrounded Service Conductor Size > E3603.1.4 Grounded Conductors
E4001.8 Devices and Luminaires, Grounded Conductors
Switches or circuit breakers shall not disconnect the grounded conductor of a circuit except where the switch or circuit breaker simultaneously ...
Residential Code 2015 of Utah > 40 Devices and Luminaires > E4001 Switches > E4001.8 Grounded Conductors
E3406.12 General Requirements, Grounded Conductor Continuity
The continuity of a grounded conductor shall not depend on connection to a metallic enclosure, raceway or cable armor. [200.2(B)] ...
Residential Code 2015 of Utah > 34 General Requirements > E3406 Electrical Conductors and Connections > E3406.12 Grounded Conductor Continuity
E3607.3.1 Services, Equipment Grounding Conductor
An equipment grounding conductor as described in Section E3908 shall be run with the supply conductors and connected to the building or structure ...
Residential Code 2015 of Utah > 36 Services > E3607 System Grounding > E3607.3 Buildings or Structures Supplied by Feeder(s) or Branch Circuit(s) > E3607.3.1 Equipment Grounding Conductor