// CODE SNIPPET
(D) Grounded Conductor Not to Be Used as an Equipment Ground
Related Code Sections
(D) Special Occupancies, Grounded Conductor Not to Be Used as an Equipment Ground
The grounded conductor shall not be used as an equipment grounding conductor for recreational vehicles or equipment within the recreational vehicle ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 551 Recreational Vehicles and Recreational Vehicle Parks > 551.76 Grounding — Recreational Vehicle Site Supply Equipment > (D) Grounded Conductor Not to Be Used as an Equipment Ground
(A) Special Equipment, Not Grounded
The direct-current cell line process power-supply conductors shall not be required to be grounded ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 668 Electrolytic Cells > 668.11 Direct-Current Cell Line Process Power Supply > (A) Not Grounded
(E) Equipment for General Use, Grounded Neutral Conductor
raceway, cable, or cable tray, or, where installed as open conductors, in close proximity to the ungrounded conductors Not used for any other circuit ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 490 Equipment Over 1000 Volts, Nominal > 490.72 Branch-Circuit Requirements > (E) Grounded Neutral Conductor
665.26 Special Equipment, Grounding and Bonding
Bonding to the equipment grounding conductor or inter-unit bonding, or both, shall be used wherever required for circuit operation, and for limiting ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 665 Induction and Dielectric Heating Equipment > 665.26 Grounding and Bonding
408.40 Equipment for General Use, Grounding of Panelboards
conductor. Where the panelboard is used with nonmetallic raceway or cable or where separate equipment grounding conductors are provided, a terminal ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 408 Switchboards, Switchgear, and Panelboards > 408.40 Grounding of Panelboards