// CODE SNIPPET
506.3.1.1 Grease Duct Materials
JUMP TO FULL CODE CHAPTER
Grease ducts serving Type I hoods shall be constructed of steel having a minimum thickness of 0.0575 inch (1.463 mm) (No. 16 gage) or stainless steel not less than 0.0450 inch (1.14 mm) (No. 18 gage) in thickness.