// CODE SNIPPET
708.0 Grade of Horizontal Drainage Piping
Go To Full Code Chapter
Horizontal drainage piping shall be run in practical alignment and a uniform slope of not less than 1/4 inch per foot (20.8 mm/m) or 2 percent toward the point of disposal provided that, where it is impractical due to the depth of the street sewer, to the structural features, or to the arrangement of a building or structure to obtain a slope of 1/4 inch per foot (20.8 mm/m) or 2 percent, such pipe or piping 4 inches (100 mm) or larger in diameter shall be permitted to have a slope of not less than 1/8 inch per foot (10.4 mm/m) or 1 percent, where first approved by the Authority Having Jurisdiction.
Related Code Sections
708.0 Sanitary Drainage, Grade of Horizontal Drainage Piping
Horizontal drainage piping shall be run in practical alignment and a uniform slope of not less than 1/4 inch per foot (20.8 mm/m) or 2 percent toward ...
P3002.3.1 Sanitary Drainage, Drainage
Drainage fittings shall have a smooth interior waterway of the same diameter as the piping served. Fittings shall conform to the type of pipe used ...
905.0 Vents, Vent Pipe Grades and Connections
vents connect to a horizontal drainage pipe, each vent pipe shall have its invert taken off above the drainage centerline of such pipe downstream ...
1220.127.116.11 Storm Drainage, Secondary Roof Drain
be a separate system of piping, independent of the primary roof drainage system. The discharge shall be above grade, in a location observable by the building ...