Section E3601 General Services
Conductors other than service conductors shall not be installed in the same service raceway or service cable in which the service conductors are installed. (230.7)
- Grounding electrode conductors or supply side bonding jumpers or conductors shall be permitted within service raceways.
- Load management control conductors having overcurrent protection shall be permitted within service raceways.
The service disconnecting means shall consist of not more than six switches or six sets of circuit breakers mounted in a single enclosure or in a group of separate enclosures. [230.71(A)]