[NY] 310.3 Gas Pipe Bonding—Listed AR-CSST
Where all of the following apply:
- All of the CSST contained in a gas piping system consists of listed AR-CSST.
- Such gas piping system is electrically continuous.
Such gas piping system shall be installed and bonded in accordance with the stricter of the following:
A gas piping system that contains only listed AR-CSST and satisfies all of the other criteria specified in Section 310.3 of this code shall be considered to be bonded to an effective ground-fault current path, and shall not be required to be directly bonded as prescribed by Section 310.2 of this code. However, nothing in Section 310.3.1 shall prohibit the bonding of any such gas piping system in any manner described in Section 250.104(B) of NFPA 70.