[NY] 310.2 Gas Pipe Bonding—CSST
A gas piping system that contains any CSST shall be electrically continuous and shall be directly bonded to the electrical service grounding electrode system. No portion of the gas piping system shall be used as or considered to be a grounding electrode or a grounding electrode conductor. CSST shall be installed and bonded in accordance with Section 310.2, and the stricter of:
- The requirements set forth in the CSST manufacturer's installation instructions.
- The requirements set forth in Sections 310.2.1, 310.2.2, 310.2.3 and 404.7 of this code.
Exception: Where all of the CSST contained in a gas piping system is listed AR-CSST and the gas piping system satisfies all of the other criteria set forth in Section 310.3 of this code, such gas piping system shall comply with Section 310.3.