// CODE SNIPPET
JUMP TO FULL CODE CHAPTER
Means shall be provided to disconnect a fuse from all sources of supply where the fuse is energized from both directions and is accessible to other than qualified persons. Switches, pullouts, or similar devices that are rated for the application shall be permitted to serve as a means to disconnect fuses from all sources of supply.
Related Code Sections
(B) Wiring and Protection, Fuses
If a switch and fuse combination is used, the fuses employed shall be capable of interrupting any current higher than the interrupting capacity ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 230 Services > 230.95 Ground-Fault Protection of Equipment > (B) Fuses
(2) Wiring and Protection, Fuses
A fuse shall be connected in series with each ungrounded conductor ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 240 Overcurrent Protection > 240.100 Feeders and Branch Circuits > (A) Location and Type of Protection > (2) Fuses
(5) Equipment for General Use, Fuses
Fuses that expel flame in opening the circuit shall be designed or arranged so that they function properly without hazard to persons or property ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 490 Equipment Over 1000 Volts, Nominal > 490.21 Circuit-Interrupting Devices > (B) Power Fuses and Fuseholders > (5) Fuses
(5) Special Occupancies, Fuses
Where general-purpose enclosures are permitted in 501.105(B)(2) through (B)(4), fuses for overcurrent protection of instrument circuits not subject ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 501 Class I Locations > 501.105 Meters, Instruments, and Relays > (B) Class I, Division 2 > (5) Fuses