// CODE SNIPPET
915.2.1 Fuel Tanks Connected to Engine-Driven Building Service Equipment
JUMP TO FULL CODE CHAPTER
Fuel tanks piped to and supplying fuel for engine-driven building service equipment may be engine mounted, located inside of a building, outside of a building, or on a roof in accordance with NFPA 37 or NFPA 30 and as modified by Section 1308 of the mechanical code for fuel oil and diesel oil tank installations.
Engine-mounted tanks located outdoors may be located in accordance with Section 4.1.4 of NFPA 37 and shall be vented in accordance with NFPA 30. Engine-mounted tanks shall be provided with adequate clearance to enable filling, maintenance, and testing, shall be safeguarded against public access, and shall be protected from impact.