// CODE SNIPPET
319.10.3 Fuel Gas Systems
JUMP TO FULL CODE CHAPTER
LP-gas containers installed on the vehicle and fuel-gas piping systems shall be inspected annually by an approved inspection agency or a company that is registered with the U.S. Department of Transportation to requalify LP-gas cylinders, to ensure that system components are free from damage, suitable for the intended service and not subject to leaking. CNG containers shall be inspected every 3 years in a qualified service facility. CNG containers shall not be used past their expiration date as listed on the manufacturer's container label. Upon satisfactory inspection, the approved inspection agency shall affix a tag on the fuel gas system or within the vehicle indicating the name of the inspection agency and the date of satisfactory inspection.
Related Code Sections
319.10.3 General Requirements, Fuel Gas Systems
LP-gas containers installed on the vehicle and fuel-gas piping systems shall be inspected annually by an approved inspection agency or a company ...
Fire Code 2018 of Kansas > 3 General Requirements > 319 Mobile Food Preparation Vehicles > 319.10 Maintenance > 319.10.3 Fuel Gas Systems
3501.5 Welding and Other Hot Work, Design and Installation of Oxygen-Fuel Gas Systems
An oxygen-fuel gas system with two or more manifolded cylinders of oxygen shall be in accordance with NFPA 51 ...
Fire Code 2018 of Kansas > 35 Welding and Other Hot Work > 3501 General > 3501.5 Design and Installation of Oxygen-Fuel Gas Systems
22.9 Special Occupancy Requirements, Oxygen-Fuel Gas Systems for Welding, Cutting, and Allied Processes
Oxygen cylinders connected to one manifold shall be limited to a total gas capacity of 6500 ft 3 (184 m 3 ). [ 51: 5.2.5 ...
Standard for the Installation of Sprinkler Systems 2016 of Kansas > 22 Special Occupancy Requirements > 22.9 Oxygen-Fuel Gas Systems for Welding, Cutting, and Allied Processes
Section G2401 Fuel Gas, (101) General
This chapter covers those fuel gas piping systems , fuel-gas appliances and related accessories, venting systems and combustion air ...
3306.2.1 Fire Safety During Construction and Demolition, Pipe Cleaning and Purging
and purging piping systems out of service, shall comply with NFPA 56. Exceptions: Compressed gas piping systems other than fuel gas piping systems ...
Fire Code 2018 of Kansas > 33 Fire Safety During Construction and Demolition > 3306 Flammable Gases > 3306.2 Cleaning With Flammable Gas > 3306.2.1 Pipe Cleaning and Purging