// CODE SNIPPET
JUMP TO FULL CODE CHAPTER
If a reliable source of supply is available at any time on a 2-hour notice, it shall be permitted to have fuel in storage sufficient for 12 hours of operation at full load.
Fuel systems using natural or manufactured gas supplied through reliable utility mains shall not be required to have fuel storage tanks unless located in seismic risk zone 3 or greater as defined in ANSI A-58.1, Building Code Requirements for Minimum Design Loads in Buildings and Other Structures.
Related Code Sections
10.14.10.1 General Safety Requirements, Fueling
Fuel tanks shall be of adequate capacity to permit uninterrupted operation during normal operating hours ...
Fire Code 2018 of Maine > 10 General Safety Requirements > 10.14 Special Outdoor Events, Carnivals, and Fairs > 10.14.10 Internal Combustion Power Sources > 10.14.10.1 Fueling
10.6.11.6 Fundamentals, Fuel
Unless otherwise required or permitted in 10.6.11.6.1 through 10.6.11.6.3, fuel shall be available in storage sufficient for 6 months of testing plus ...
National Fire Alarm and Signaling Code 2019 of Maine > 10 Fundamentals > 10.6 Power Supplies > 10.6.11 Engine-Driven Generators > 10.6.11.6 Fuel
188.8.131.52 Grandstands and Bleachers, Folding and Telescopic Seating, Tents, and Membrane Structures, Fueling
Fuel tanks shall be of adequate capacity to permit uninterrupted operation during normal operating hours. Refueling shall be conducted only when ...
Fire Code 2018 of Maine > 25 Grandstands and Bleachers, Folding and Telescopic Seating, Tents, and Membrane Structures > 25.1 General > 25.1.12 Generators > 184.108.40.206 Fueling
10.18.7 General Safety Requirements, Fueled Equipment
Fueled equipment, including but not limited to motorcycles, mopeds, lawn-care equipment, and portable cooking equipment, shall not be stored ...
Fire Code 2018 of Maine > 10 General Safety Requirements > 10.18* Storage of Combustible Materials > 10.18.7 Fueled Equipment
220.127.116.11 Safeguarding Construction, Alteration, and Demolition Operations, Fuel System
Fuel containers shall be constructed and approved for the use for which they were designed ...
Fire Code 2018 of Maine > 16 Safeguarding Construction, Alteration, and Demolition Operations > 16.7 Tar Kettles and Rubberized Asphalt Melters > 16.7.2 Tar Kettles > 18.104.22.168 Fuel System