// CODE SNIPPET
Section 706 Forced Combustion Air Supply
JUMP TO FULL CODE CHAPTER
Where all combustion air and dilution air is provided by a mechanical forced-air system, the combustion air and dilution air shall be supplied at the minimum rate of 1 cfm per 2,400 Btu/h [0.00067 m3/(s • kW)] of combined input rating of all the fuel-burning appliances served. Combustion air rates shall also comply with any applicable rules of the New York City Department of Environmental Protection.
Related Code Sections
Section 706 Combustion Air, Forced Combustion Air Supply
Where all combustion air and dilution air is provided by a mechanical forced-air system, the combustion air and dilution air shall be supplied ...
§27-881 Chimneys and Gas Vents, Draft Hoods
or forced venting, shall be installed with a draft hood or with a barometric damper. (b) The draft hood supplied with, or forming a part of, vented ...
§27-807 Heating and Combustion Equipment, Air Supply
(a) Oil fuels. The air supply for equipment burning fuel oil shall comply with the requirements in applicable standards in reference standard RS-14 ...
*605.3 Specific Appliances, Combustion Air Supply
The requirements of the New York City Energy Conservation Code concerning combustion air supply shall be followed. *Section FGC 605.3 was amended ...
NYC Fuel Gas Code 2008 > 6 Specific Appliances > 605 Vented Gas Fireplace Heaters > *605.3 Combustion Air Supply