// CODE SNIPPET
3129B.1 Flow Rates
Related Code Sections
3129B.1 [DPH] Public Pools, Flow Rates
The filtration rate shall not exceed 3 gallons per minute per square foot (122.24 L/m per m 2 ) of filter area. The backwash rate shall not be less ...
Los Angeles Building Code > 31B [DPH] Public Pools > 3129B Rapid Sand Pressure Filters > 3129B.1 Flow Rates
3130B.1 [DPH] Public Pools, Flow Rates
The filtration rate for both pressure and vacuum diatomaceous earth filters shall not exceed 2 gallons per minute per square foot (81.49 L/m per m 2 ...
Los Angeles Building Code > 31B [DPH] Public Pools > 3130B Diatomaceous Earth Filters > 3130B.1 Flow Rates
3131B.1 [DPH] Public Pools, Flow Rates
Maximum and minimum flow rates for backwash and filtration shall be maintained according to the applicable requirements established by the NSF/ANSI ...
Los Angeles Building Code > 31B [DPH] Public Pools > 3131B High-Rate Sand Filters > 3131B.1 Flow Rates
2309.6.1.2.1.3 Motor Fuel-Dispensing Facilities and Repair Garages, Maximum Flow Rate
The maximum rate of hydrogen flow through the vent pipe system shall not exceed 1,000 cfm at NTP (0.47 m 3 /s) and shall be controlled by means ...
2017 LA City Fire Code > 23 Motor Fuel-Dispensing Facilities and Repair Garages > 2309 Hydrogen Motor Fuel-Dispensing and Generation Facilities > 2309.6 Defueling of Hydrogen From Fuel Storage Containers > 2309.6.1 Methods of Discharge > 2309.6.1.2 Atmospheric Venting of Hydrogen From Fuel Storage Containers > 2309.6.1.2.1 Defueling Equipment > 2309.6.1.2.1.3 Maximum Flow Rate
6188.8.131.52 Water Supply and Distribution, System Flow Rate
The flow rate used for sizing the sprinkler piping system shall be based on the following: The flow rate for a room having only one sprinkler ...
Los Angeles Plumbing Code > 6 Water Supply and Distribution > 612.0 Residential Fire Sprinkler Systems > 612.5 Sprinkler Piping Design > 612.5.1 Determining System Design Flow > 6184.108.40.206 System Flow Rate