// CODE SNIPPET
M1601.4.10 Floor Register Location
Related Code Sections
M1601.4.10 Duct Systems, Floor Register Location
Floor registers located in room or spaces containing water closets shall be located a minimum of 3 feet (914 mm) from the water closet. R ...
2015 Michigan Residential Code > 16 Duct Systems > M1601 Duct Construction > M1601.4 Installation > M1601.4.10 Floor Register Location
M1408.5 Heating and Cooling Equipment and Appliances, Installation
in which the register of the floor furnace is located. Floor furnaces shall be supported independently of the furnace floor register. Floor ...
2015 Michigan Residential Code > 14 Heating and Cooling Equipment and Appliances > M1408 Vented Floor Furnaces > M1408.5 Installation
910.2 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment, Placement
element from any such room or space. With the exception of wall register models, a floor furnace shall not be placed closer than 6 inches (152 mm ...
2015 Michigan Mechanical Code > 9 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment > 910 Floor Furnaces > 910.2 Placement
G2437.2 Fuel Gas, (609.2) Placement
(457 mm) from two adjoining sides of the floor furnace register to walls shall be provided to eliminate the necessity of occupants walking over ...
2015 Michigan Residential Code > 24 Fuel Gas > G2437 (609) Floor Furnaces > G2437.2 (609.2) Placement
603.18.1 Duct Systems, Floor Registers
Floor registers shall resist, without structural failure, a 200-pound (90.8 kg) concentrated load on a 2-inch-diameter (51 mm) disc applied ...
2015 Michigan Mechanical Code > 6 Duct Systems > 603 Duct Construction and Installation > 603.18 Registers, Grilles and Diffusers > 603.18.1 Floor Registers