// CODE SNIPPET
(7) Flexible Cord Storage
Related Code Sections
(7) Special Occupancies, Flexible Cord Storage
A storage device for the flexible cord shall be provided and shall not subject the cord to bending at a radius of less than 75 mm (3 in.) ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.61 Wiring and Equipment > (A) Within Hazardous (Classified) Anesthetizing Locations > (7) Flexible Cord Storage
680.56 Special Equipment, Cord-And-Plug-Connected Equipment
Flexible cord immersed in or exposed to water shall be of a type for extra-hard usage ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 680 Swimming Pools, Fountains, and Similar Installations > 680.56 Cord-And-Plug-Connected Equipment
(C) Wiring and Protection, Flexible Cords
An insulated conductor that is intended for use as a grounded conductor, where contained within a flexible cord, shall be identified by a white ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 200 Use and Identification of Grounded Conductors > 200.6 Means of Identifying Grounded Conductors > (C) Flexible Cords
(C) Wiring and Protection, Flexible Cord
Equipment grounding conductors in flexible cords shall be insulated and shall have a continuous outer finish that is either green or green with one ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 250 Grounding and Bonding > 250.119 Identification of Equipment Grounding Conductors > (C) Flexible Cord
(1) Wiring Methods and Materials, Flexible Cord
A box shall be supported from a multiconductor cord or cable in an approved manner that protects the conductors against strain, such as a strain ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 314 Outlet, Device, Pull, and Junction Boxes; Conduit Bodies; Fittings; And Handhole Enclosures > 314.23 Supports > (H) Pendant Boxes > (1) Flexible Cord