// CODE SNIPPET
188.8.131.52.2 Flammable Refrigerants
JUMP TO FULL CODE CHAPTER
Systems containing flammable refrigerants shall discharge vapor to the atmosphere in accordance with the following:
- For refrigerants having a density equal to or greater than the density of air, discharge shall be through an approved treatment system in accordance with or flaring system in accordance with 184.108.40.206.
- For refrigerants having a density less than the density of air, discharge to the atmosphere shall be permitted, provided that the point of discharge is located outside of the structure at not less than 15 ft (4.6 m) above the adjoining grade level and not less than 20 ft (6.1 m) from any window, ventilation opening, or exit.
Related Code Sections
1106.4 Refrigeration, Flammable Refrigerants
Where refrigerants of Groups A2, A3, B2 and B3 are used, the machinery room shall conform to the Class 1, Division 2, hazardous location ...
Mechanical Code 2015 of West Virginia > 11 Refrigeration > 1106 Machinery Room, Special Requirements > 1106.4 Flammable Refrigerants
220.127.116.11.2 Mechanical Refrigeration, Flammable Refrigerants
Systems containing flammable refrigerants shall discharge vapor to the atmosphere in accordance with the following: For refrigerants having ...
Fire Code 2018 of West Virginia > 53 Mechanical Refrigeration > 53.2 Safety Features > 53.2.2 Treatment, Flaring, and Diffusion Systems for Refrigerant Discharge > 18.104.22.168 Required Systems > 22.214.171.124.2 Flammable Refrigerants
1105.9 Refrigeration, Emergency Pressure Control System
Permanently installed refrigeration systems containing more than 6.6 pounds (3 kg) of flammable, toxic or highly toxic refrigerant or ammonia shall ...
Mechanical Code 2015 of West Virginia > 11 Refrigeration > 1105 Machinery Room, General Requirements > 1105.9 Emergency Pressure Control System
126.96.36.199.1 Mechanical Refrigeration,
Flammable and combustible materials shall not be stored in refrigeration machinery rooms except for incidental materials necessary for the safe ...
Fire Code 2018 of West Virginia > 53 Mechanical Refrigeration > 53.3 Operations, Maintenance, Testing, and Decommissioning > 53.3.1 Operations and Maintenance > 188.8.131.52 Storage in Machinery Rooms > 184.108.40.206.1
220.127.116.11.2 Marijuana Growing, Processing, or Extraction Facilities, Equipment
Refrigerators, freezers, and other cooling equipment used to store or cool flammable liquids shall be listed ...
Fire Code 2018 of West Virginia > 38 Marijuana Growing, Processing, or Extraction Facilities > 38.6* Processing or Extraction > 38.6.1 General > 18.104.22.168 Systems, Equipment, and Processes > 22.214.171.124.2 Equipment