// CODE SNIPPET
3504.1.4 Flammable Gas Storage of More Than 3,500 SCF (99.12 M3)
JUMP TO FULL CODE CHAPTER
Except as otherwise provided in the rules with respect to construction sites, a storage room may contain more than one storage area, provided that each storage area does not exceed 3,500 SCF (99.12 m3) and storage areas are separated from each other by at least 50 feet (15 240 mm) or an approved masonry barrier having a minimum fire resistance rating of 2 hours. Each such storage area shall additionally comply with the requirements of FC 3504.1.2 and 3504.1.3.