// CODE SNIPPET
P-409.5 Fixture Joints
JUMP TO FULL CODE CHAPTER
The joints between drainage pipes and water closets, trap standard service sinks, pedestal urinals, or other floor outlet connected fixtures with trap standards shall be made to the drainage piping by means of brass or iron flanges, caulked, soldered, threaded or by use of a gasket in accordance with Section P-305. The connection shall be bolted to the earthenware by means of a brass bolt between the base of the fixture and the connection. The floor flange shall be set on an approved, firm base. When supported on wood floor construction, flanges shall be securely fastened to the floor construction. Floor flanges shall not be less than 1/4-inch thick when of cast iron or galvanized malleable iron, and not less than 1/8-inch thick when of brass or hard lead used for repair only. The joints between roof drains and floor drains shall be connected to the drain lines in accordance with this Chapter or by using a gasket in accordance with Section P-305.
Related Code Sections
P-409.5 Joints, Fixture Joints
The joints between drainage pipes and water closets, trap standard service sinks, pedestal urinals, or other floor outlet connected fixtures ...
405.6 Fixtures, Faucets and Fixture Fittings, Water-Tight Joints
Joints formed where fixtures come in contact with walls or floors shall be sealed ...
Plumbing Code 2018 of Philadelphia > 4 Fixtures, Faucets and Fixture Fittings > 405 Installation of Fixtures > 405.6 Water-Tight Joints
605.2.1 Water Supply and Distribution, Lead Content of Drinking Water Pipe and Fittings
Pipe, pipe fittings, joints, valves, faucets and fixture fittings utilized to supply water for drinking or cooking purposes shall comply with NSF 372 ...
Plumbing Code 2018 of Philadelphia > 6 Water Supply and Distribution > 605 Materials, Joints and Connections > 605.2 Lead Content of Water Supply Pipe and Fittings > 605.2.1 Lead Content of Drinking Water Pipe and Fittings
520.63 Special Occupancies, Bracket Fixture Wiring
that extend through scenery and without joint or splice in canopy of fixture back and terminate in an approved-type stage connector located, where ...
National Electrical Code 2014 of Philadelphia > 5 Special Occupancies > 520 Theaters, Audience Areas of Motion Picture and Television Studios, Performance Areas, and Similar Locations > 520.63 Bracket Fixture Wiring