// CODE SNIPPET
704.0 Fixture Connections (Drainage)
JUMP TO FULL CODE CHAPTER
Drainage piping shall be provided with approved inlet fittings for fixture connections, correctly located according to the size and type of fixture proposed to be connected.
Pot sinks, scullery sinks, dishwashing sinks, silverware sinks, and other similar fixtures shall be connected directly to the drainage system. A floor drain shall be provided adjacent to the fixture, and the fixture shall be connected on the sewer side of the floor drain trap, provided that no other drainage line is connected between the floor drain waste connection and the fixture drain. The fixture and floor drain shall be trapped and vented in accordance with this code.
Related Code Sections
704.0 Sanitary Drainage, Fixture Connections (Drainage)
Drainage piping shall be provided with approved inlet fittings for fixture connections, correctly located according to the size and type of fixture ...
907.1 Vents, Drainage Stack
terminal and connect to the drainage stack at or immediately below the lowest fixture drain. Each such vent stack shall also be connected ...
Uniform Plumbing Code 2018 of Nevada > 9 Vents > 907.0 Vent Stacks and Relief Vents > 907.1 Drainage Stack
C 601.2 Alternate Plumbing Systems, Stack Size
) stack. Stacks shall be uniformly sized based on the total connected drainage fixture unit load, with no reductions in size. TABLE C 601.2 SINGLE ...
Uniform Plumbing Code 2018 of Nevada > C Alternate Plumbing Systems > C 601.0 Single-Stack Vent System > C 601.2 Stack Size
Section P2704 Plumbing Fixtures, Slip-Joint Connections
Slip-joint connections shall be installed only for tubular waste piping and only between the trap outlet of a fixture and the connection ...