// CODE SNIPPET
188.8.131.52 Fixed Fire Control Equipment for Tank Buildings
JUMP TO FULL CODE CHAPTER
Where the need is indicated by the hazards of storage or exposure as determined by 184.108.40.206, fixed protection shall be required utilizing approved foam, foam-water sprinkler systems, sprinkler systems, water spray systems, deluge systems, gaseous extinguishing systems, dry chemical extinguishing systems, fire-resistive materials, or a combination of these. [30:220.127.116.11]
If provided, fire control systems shall be designed, installed, and maintained in accordance with the following NFPA standards:
- NFPA 11, Standard for Low-, Medium-, and High-Expansion Foam
- NFPA 12, Standard on Carbon Dioxide Extinguishing Systems
- NFPA 12A, Standard on Halon 1301 Fire Extinguishing Systems
- NFPA 13, Standard for the Installation of Sprinkler Systems
- NFPA 15, Standard for Water Spray Fixed Systems for Fire Protection
- NFPA 16, Standard for the Installation of Foam-Water Sprinkler and Foam-Water Spray Systems
- NFPA 17, Standard for Dry Chemical Extinguishing Systems
- NFPA 25, Standard for the Inspection, Testing, and Maintenance of Water-Based Fire Protection Systems
Related Code Sections
18.104.22.168 Flammable and Combustible Liquids, Fixed Fire Control Equipment for Tank Buildings
A reliable water supply or other suitable fire control agent shall be available in pressure and quantity to meet the fire demands indicated ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.24 Storage Tank Buildings > 66.24.6 Fire Protection for Storage Tank Buildings > 22.214.171.124 Fixed Fire Control Equipment for Tank Buildings
66.22.8 Flammable and Combustible Liquids, Fire Control
A fire-extinguishing system in accordance with an applicable NFPA standard shall be provided or shall be available for vertical atmospheric fixed ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.22 Storage of Liquids in Tanks — Aboveground Storage Tanks > 66.22.8 Fire Control
126.96.36.199.4 Fire Protection Systems, Impaired Equipment
storage tanks Water spray fixed systems Foam-water sprinkler systems Water mist systems Fire service control valves Water supply [ 25 ...
Fire Code 2018 of West Virginia > 13 Fire Protection Systems > 13.3 Automatic Sprinklers > 13.3.3 Inspection, Testing, and Maintenance > 188.8.131.52 Impairments > 184.108.40.206.4 Impaired Equipment
66.24.6 Flammable and Combustible Liquids, Fire Protection for Storage Tank Buildings
connections from sprinkler systems using combination spray and straight stream nozzles to permit effective fire control. [ 30: 220.127.116.11 ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.24 Storage Tank Buildings > 66.24.6 Fire Protection for Storage Tank Buildings
424.73 Equipment for General Use, Overtemperature Limit Control
Each boiler designed so that in normal operation there is no change in state of the heat transfer medium shall be equipped with a temperature ...
National Electrical Code 2017 of West Virginia > 4 Equipment for General Use > 424 Fixed Electric Space-Heating Equipment > 424.73 Overtemperature Limit Control