// CODE SNIPPET
904.10.7 Fixed Emergency Forced Ventilation
JUMP TO FULL CODE CHAPTER
When the protected area is normally occupied, a fixed emergency forced ventilation system sufficient to accomplish at least six air changes per hour of the flooded protected area shall be provided unless all of the following apply:
- The clean agent fire extinguishing system is used to extinguish a Class A fire.
- The design concentration does not exceed the "no observable adverse effect level" for halocarbon agents, or "no effect level" for inert gas agents as defined in NFPA 2001, as modified by FC Appendix B.
- If other than inert gas agents are used, the quantity of the thermal decomposition products formed from such agents is below the dangerous toxic load (DTL) for humans as described in Meldrum's "Toxicology of Substances in Relation to Major Hazards: Hydrogen Fluoride" (HMSO, London, 1993). Upon request, documentation of hazard assessment of thermal decomposition products formed from such agents shall be filed with the department.