// CODE SNIPPET
322.214.171.124 Fire Separation Distances
Related Code Sections
1403.12.2 Exterior Walls, Fire Separation Distance
The fire separation distance between a building with polypropylene siding and the adjacent building shall be not less than 10 feet (3048 mm) ...
Building Code 2018 of Illinois > 14 Exterior Walls > 1403 Materials > 1403.12 Polypropylene Siding > 1403.12.2 Fire Separation Distance
3126.96.36.199 Special Construction, Fire Separation Distances
Ground-mounted photovoltaic systems shall be subject to the fire separation distance requirements determined by the local jurisdiction ...
Building Code 2018 of Illinois > 31 Special Construction > 3111 Solar Energy Systems > 3111.3 Photovoltaic Solar Energy Systems > 3111.3.5 Ground-Mounted Photovoltaic Systems > 3188.8.131.52 Fire Separation Distances
406.5.6 Special Detailed Requirements Based on Occupancy and Use, Fire Separation Distance
Exterior walls and openings in exterior walls shall comply with Tables 601 and 602. The distance to an adjacent lot line shall be determined ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 406 Motor-Vehicle-Related Occupancies > 406.5 Open Parking Garages > 406.5.6 Fire Separation Distance
415.6 Special Detailed Requirements Based on Occupancy and Use, Fire Separation Distance
Regardless of any other provisions, buildings containing Group H occupancies shall be set back to the minimum fire separation distance as set ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.6 Fire Separation Distance
1406.11.4.1 Exterior Walls, Minimum Fire Separation Distance
MCM shall not be installed on any wall with a fire separation distance less than 30 feet (9 144 mm). Exception: Where the building is equipped ...
Building Code 2018 of Illinois > 14 Exterior Walls > 1406 Metal Composite Materials (MCM) > 1406.11 Alternate Conditions > 1406.11.4 Installations Up to 75 Feet in Height (Option 2) > 1406.11.4.1 Minimum Fire Separation Distance