// CODE SNIPPET
A-402.10.1.6 Fire-Resistant and Smoke-Resistant Penetrations
JUMP TO FULL CODE CHAPTER
Protection of joints and penetrations in fire-resistance-rated assemblies, smoke barriers and smoke partitions shall not be concealed from view until inspected and approved.
Related Code Sections
A-402.10.1.6 Inspections, Fire-Resistant and Smoke-Resistant Penetrations
Protection of joints and penetrations in fire-resistance-rated assemblies, smoke barriers and smoke partitions shall not be concealed from view until ...
Philadelphia Administrative Code > 4 Inspections > A-402 Permit Inspections > A-402.10 Required Inspections > A-402.10.1 Building Permits > A-402.10.1.6 Fire-Resistant and Smoke-Resistant Penetrations
Section 703 Fire and Smoke Protection Features, Penetrations
Materials and firestop systems used to protect membrane and through penetrations in fire-resistance-rated construction and construction installed ...
607.5.2 Duct Systems, Fire Barriers
with the operation of the smoke control system. Such walls are penetrated by ducted HVAC systems, have a required fire-resistance rating of 1 hour or less ...
2018 Philadelphia Mechanical Code > 6 Duct Systems > 607 Duct and Transfer Openings > 607.5 Where Required > 607.5.2 Fire Barriers
717.5.2 Fire and Smoke Protection Features, Fire Barriers
listed smoke damper designed to resist the passage of smoke shall be provided at each point a duct or air transfer opening penetrates a fire barrier ...
2018 Philadelphia Building Code > 7 Fire and Smoke Protection Features > 717 Ducts and Air Transfer Openings > 717.5 Where Required > 717.5.2 Fire Barriers
703.1 Fire-Resistance-Rated Construction, Maintenance
The required fire-resistance rating of fire-resistance-rated construction (including walls, firestops, shaft enclosures, partitions, smoke ...
Philadelphia Fire Code > 7 Fire-Resistance-Rated Construction > 703 Fire-Resistance-Rated Construction > 703.1 Maintenance