// CODE SNIPPET
Article 2 Fire Protection Test Procedures
JUMP TO FULL CODE CHAPTER
Samples of all materials or assemblies of materials required by this code to have a fire-resistance rating, fire-protection rating, or flame spread rating, or required to be noncombustible, fire-retardant treated, or slow burning, shall be tested under the applicable test procedures specified herein, in accordance with the acceptance requirements of section 27-131 of article seven of subchapter one of this chapter. The fire-resistance rating of materials and assemblies listed in reference standard RS 5-1 may be used to determine conformance with the fire resistance requirements of this code. In addition to the performance results, test reports shall give all technical data pertaining to the nature of the constituent materials, such as the physical properties, chemical composition and properties, coefficient of expansion, thicknesses of materials, etc. Except as listed in reference standard RS 5-1, any assembly using a component having a structural base of noncombustible material covered with an integrally manufactured combustible surfacing material, shall be approved for fire-resistance rating.
Related Code Sections
Article 2 Fire Protection Construction Requirements, Fire Protection Test Procedures
rating, or required to be noncombustible, fire-retardant treated, or slow burning, shall be tested under the applicable test procedures specified ...
NYC 1968 Code (Vol I) > 5 Fire Protection Construction Requirements > 2 Fire Protection Test Procedures
715.3 Fire and Smoke Protection Features, Alternative Methods for Determining Fire Protection Ratings
of opening protective designs having fire protection ratings as determined by the test procedures set forth in NFPA 252, NFPA 257 or UL 9. Alternative ...
NYC Building Code 2014 > 7 Fire and Smoke Protection Features > 715 Opening Protectives > 715.3 Alternative Methods for Determining Fire Protection Ratings
§27-329 Fire Protection Construction Requirements, Opening Protectives
Opening protectives, including frames, self-closing devices, and hardware, shall be classified as to fire-protection rating in accordance ...
NYC 1968 Code (Vol I) > 5 Fire Protection Construction Requirements > 3 Fire-Resistance Requirements > §27-329 Opening Protectives
312.10.2 General Regulations, Testing
prevention assemblies, and double check detector fire protection backflow prevention assemblies shall be tested at the time of installation, immediately after ...
NYC Plumbing Code 2014 > 3 General Regulations > 312 Tests and Inspections > 312.10 Inspection and Testing of Backflow Prevention Assemblies > 312.10.2 Testing
312.9.2 General Regulations, Testing
and the city department of environmental protection for additional testing requirements. The testing procedure shall be performed in accordance ...
NYC Plumbing Code 2008 > 3 General Regulations > 312 Tests and Inspections > 312.9 Inspection and Testing of Backflow Prevention Assemblies > 312.9.2 Testing