[F] 909.16 Fire Fighter's Smoke Control Panel
Fans within the building shall be shown on the fire fighter's control panel. A clear indication of the direction of airflow and the relationship of components shall be displayed. Status indicators shall be provided for all smoke control equipment, annunciated by fan and zone, and by pilot-lamp-type indicators as follows:
- Fans, dampers and other operating equipment in their normal status—WHITE.
- Fans, dampers and other operating equipment in their off or closed status—RED.
- Fans, dampers and other operating equipment in their on or open status—GREEN.
- Fans, dampers and other operating equipment in a fault status—YELLOW/AMBER.
The fire fighter's control panel shall provide control capability over the complete smoke control system equipment within the building as follows:
- ON-AUTO-OFF control over each individual piece of operating smoke control equipment that can be controlled from other sources within the building. This includes stairway pressurization fans; smoke exhaust fans; supply, return and exhaust fans; elevator shaft fans and other operating equipment used or intended for smoke control purposes.
- OPEN-AUTO-CLOSE control over individual dampers relating to smoke control and that are controlled from other sources within the building.
- ON-OFF or OPEN-CLOSE control over smoke control and other critical equipment associated with a fire or smoke emergency and that can only be controlled from the fire fighter's control panel.
The fire-fighter's control panel actions shall be as follows:
- Only the AUTO position of each three-position fire-fighter's control panel switch shall allow automatic or manual control action from other control points within the building. The AUTO position shall be the NORMAL, nonemergency, building control position. Where a fire fighter's control panel is in the AUTO position, the actual status of the device (on, off, open, closed) shall continue to be indicated by the status indicator described in Section 909.16.1. Where directed by an automatic signal to assume an emergency condition, the NORMAL position shall become the emergency condition for that device or group of devices within the zone. Control actions shall not require the smoke control system to assume more than one configuration at any one time.