// CODE SNIPPET
5906.5.7 Fire-Extinguishing Materials
JUMP TO FULL CODE CHAPTER
Fire-extinguishing materials shall be provided for every operator performing machining, grinding or other processing operation on magnesium as follows:
- Within 30 feet (9144 mm), a supply of extinguishing materials in an approved container with a hand scoop or shovel for applying the material; or
- Within 75 feet (22 860 mm), a portable fire extinguisher complying with Section 906.
All extinguishing materials shall be approved for use on magnesium fires. Where extinguishing materials are stored in cabinets or other enclosed areas, the enclosures shall be openable without the use of a key or special knowledge.
Related Code Sections
5906.5.7 Flammable Solids, Fire-Extinguishing Materials
Fire-extinguishing materials shall be provided for every operator performing machining, grinding or other processing operation on magnesium ...
Fire Code 2012 of Tennessee > 59 Flammable Solids > 5906 Magnesium > 5906.5 Use of Magnesium > 5906.5.7 Fire-Extinguishing Materials
Section 1504 Construction Safeguards, Fire Extinguishers
where combustible materials have accumulated. In every storage and construction shed. Additional portable fire extinguishers shall be provided ...
Section 3309 Safeguards During Construction, Fire Extinguishers
All structures under construction, alteration or demolition shall be provided with no fewer than one approved portable fire extinguisher ...
Section 3315 Fire Safety During Construction and Demolition, Portable Fire Extinguishers
Structures under construction, alteration or demolition shall be provided with not less than one approved portable fire extinguisher ...
Fire Code 2012 of Tennessee > 33 Fire Safety During Construction and Demolition > 3315 Portable Fire Extinguishers
5003.8.5.3 Hazardous Materials—General Provisions, Fire-Extinguishing System
Exhausted enclosures where flammable materials are used shall be protected by an approved automatic fire-extinguishing system in accordance ...
Fire Code 2012 of Tennessee > 50 Hazardous Materials—General Provisions > 5003 General Requirements > 5003.8 Construction Requirements > 5003.8.5 Exhausted Enclosures > 5003.8.5.3 Fire-Extinguishing System