// CODE SNIPPET
907.3.2 Fire Alarm System Control Panel
Related Code Sections
Reference Standard 17 Fire, Alarms, Detection and Extinguishing Equipment [PDF] (page 47)
in existing buildings may either be installed as part of an interior fire alarm and signal system or be connected to an approved strobe control panel. 3 ...
NYC 1968 Code (Vol II) [PDF] > Reference Standard 17 Fire, Alarms, Detection and Extinguishing Equipment
911.1.5 Fire Protection Systems, Required Features
: Fire alarm control unit: The emergency voice/alarm communication system control unit. The two-way communications system. Fire ...
NYC Building Code 2014 > 9 Fire Protection Systems > 911 Fire Command Center > 911.1 General > 911.1.5 Required Features
912.2.3 Fire Protection Systems, Operation
, or fire alarm panel when a fire command center is not required. Such control center or panel shall display a graphic indicating the portions ...
NYC Building Code 2008 > 9 Fire Protection Systems > 912 Post-Fire Smoke Purge Systems > 912.2 Post-Fire Smoke Purge Systems in Occupancy Groups Other Than R-2 > 912.2.3 Operation
907.1 Fire Protection Systems, General
10. Fire alarm sequence of operation for the fire alarm control panel and the central station transmitter. 11. The interface ...
NYC Building Code 2008 > 9 Fire Protection Systems > 907 Fire Alarm and Detection Systems > 907.1 General
Section 911 Fire Protection Systems, Fire Command Center
be located in the lobby of the building on the entrance floor as part of the fire alarm control panel, elevator control panel or immediately adjacent ...