C408.2.5.2 Final Commissioning Report
A report of test procedures and results identified as "Final Commissioning Report" shall be delivered to the building owner or owner's authorized agent. The report shall be organized with mechanical system and service hot water system findings in separate sections to allow independent review. The report shall include the following:
- Results of functional performance tests.
- Disposition of deficiencies found during testing, including details of corrective measures used or proposed.
- Functional performance test procedures used during the commissioning process including measurable criteria for test acceptance, provided herein for repeatability.
Exception: Deferred tests that cannot be performed at the time of report preparation due to climatic conditions.