// CODE SNIPPET
M2203.3 Fill Piping
JUMP TO FULL CODE CHAPTER
Fill piping shall terminate outside of buildings at a point not less than 2 feet (610 mm) from any building opening at the same or lower level. Fill openings shall be equipped with a tight metal cover.
Related Code Sections
1305.6 Fuel Oil Piping and Storage, Fill Piping
A fill pipe shall terminate outside of a building at a point not less than 2 feet (610 mm) from any building opening at the same or lower level. A ...
Mechanical Code 2018 of Kansas > 13 Fuel Oil Piping and Storage > 1305 Fuel Oil System Installation > 1305.6 Fill Piping
M2203.3 Special Piping and Storage Systems, Fill Piping
Fill piping shall terminate outside of buildings at a point not less than 2 feet (610 mm) from any building opening at the same or lower level. Fill ...
Residential Code 2018 of Kansas > 22 Special Piping and Storage Systems > M2203 Installation > M2203.3 Fill Piping
2306.6.2.2 Motor Fuel-Dispensing Facilities and Repair Garages, Fill-Pipe Connections
The fill pipe for above-ground tanks shall be provided with a means for making a direct connection to the tank vehicle's fuel-delivery hose so ...
Fire Code 2018 of Kansas > 23 Motor Fuel-Dispensing Facilities and Repair Garages > 2306 Flammable and Combustible Liquid Motor Fuel-Dispensing Facilities > 2306.6 Piping, Valves, Fittings and Ancillary Equipment for Use With Flammable or Combustible Liquids > 2306.6.2 Piping, Valves, Fittings and Ancillary Equipment for Above-Ground Tanks for Class I, II and III Liquids > 2306.6.2.2 Fill-Pipe Connections
5704.2.9.5.2 Flammable and Combustible Liquids, Fill Pipe Connections
Fill pipe connections for tanks storing Class I, II and IIIA liquids and Class IIIB liquids connected to fuel-burning equipment shall ...
Fire Code 2018 of Kansas > 57 Flammable and Combustible Liquids > 5704 Storage > 5704.2 Tank Storage > 5704.2.9 Above-Ground Tanks > 5704.2.9.5 Above-Ground Tanks Inside of Buildings > 5704.2.9.5.2 Fill Pipe Connections
184.108.40.206.5 Installation Requirements,
Water-filled piping shall be permitted to be installed in areas where the temperature is less than 40°F (4°C) when heat loss calculations performed ...
Standard for the Installation of Sprinkler Systems 2016 of Kansas > 8 Installation Requirements > 8.16 Piping Installation > 8.16.4 Protection of Piping > 220.127.116.11 Protection of Piping Against Freezing > 18.104.22.168.5