// CODE SNIPPET
118.104.22.168 Fault Condition
JUMP TO FULL CODE CHAPTER
The hazard mitigation analysis shall evaluate the consequences of the following failure modes, and others deemed necessary by the fire code official. Only single-failure modes shall be considered.
- Thermal runaway condition in a single-battery storage rack, module or array.
- Failure of any energy management system.
- Failure of any required ventilation system.
- Voltage surges on the primary electric supply.
- Short circuits on the load side of the stationary battery storage system.
- Failure of the smoke detection, fire-extinguishing or gas detection system.
- Spill neutralization not being provided or failure of the secondary containment system.
Related Code Sections
122.214.171.124 Energy Systems, Fault Condition
Only single-failure modes shall be considered. Thermal runaway condition in a single-battery storage rack, module or array. Failure of any ...
Fire Code 2018 of Colorado > 12 Energy Systems > 1206 Electrical Energy Storage Systems > 1206.2 Stationary Storage Battery Systems > 1206.2.3 Hazard Mitigation Analysis > 1126.96.36.199 Fault Condition
1188.8.131.52 Energy Systems, Fault Condition
thermal runaway condition in a single ESS rack, module or unit. Failure of any battery (energy) management system. Failure of any required ventilation ...
Fire Code 2021 of Colorado > 12 Energy Systems > 1207 Electrical Energy Storage Systems (ESS) > 1207.1 General > 1207.1.4 Hazard Mitigation Analysis > 1184.108.40.206 Fault Condition
10.19.2 Fundamentals, Two-Way Telephone Communications Circuits
Two-way telephone communications circuit installation conductors shall be monitored for open circuit fault conditions that would cause the telephone ...
National Fire Alarm and Signaling Code 2013 of Colorado > 10 Fundamentals > 10.19 Monitoring Integrity of In-Building Fire Emergency Voice/Alarm Communications Systems > 10.19.2 Two-Way Telephone Communications Circuits
12.6.14 Circuits and Pathways,
Monitoring for integrity of the installation conductors for a ground-fault condition shall not be required for the communications and transmission ...
National Fire Alarm and Signaling Code 2013 of Colorado > 12 Circuits and Pathways > 12.6* Monitoring Integrity and Circuit Performance of Installation Conductors and Other Signaling Channels. (SIG-FUN) > 12.6.14
A single audible trouble signal shall be permitted to annunciate multiple fault conditions ...
National Fire Alarm and Signaling Code 2013 of Colorado > 10 Fundamentals > 10.15 Trouble Signals > 10.15.4