// CODE SNIPPET
188.8.131.52.3 F Ratings
Related Code Sections
184.108.40.206.3 Features of Fire Protection, F Ratings
Firestop systems and devices shall have an F rating of not less than 1 hour, and not less than the required fire resistance rating of the fire ...
Life Safety Code 2018 of Kansas > 8 Features of Fire Protection > 8.3 Fire Barriers > 8.3.4 Penetrations > 220.127.116.11* Firestop Systems and Devices Required > 18.104.22.168.3 F Ratings
(A) Wiring Methods and Materials, Thermal Insulation
Armored cable installed in thermal insulation shall have conductors rated at 90°C (194°F). The ampacity of cable installed in these applications ...
National Electrical Code 2017 of Kansas > 3 Wiring Methods and Materials > 320 Armored Cable: Type AC > 320.80 Ampacity > (A) Thermal Insulation
E3705.4.4 Branch Circuit and Feeder Requirements, Conductors of Type NM Cable
Conductors in NM cable assemblies shall be rated at 90°C (194°F). Types NM, NMC, and NMS cable identified by the markings NM-B, NMC-B, and NMS-B meet ...
Residential Code 2018 of Kansas > 37 Branch Circuit and Feeder Requirements > E3705 Conductor Sizing and Overcurrent Protection > E3705.4 Temperature Limitations > E3705.4.4 Conductors of Type NM Cable
334.80 Wiring Methods and Materials, Ampacity
(140°F) rated conductor. The 90°C (194°F) rating shall be permitted to be used for ampacity adjustment and correction calculations, provided the final ...
National Electrical Code 2017 of Kansas > 3 Wiring Methods and Materials > 334 Nonmetallic-Sheathed Cable: Types NM, NMC, and NMS > 334.80 Ampacity
722.214.171.124 Fire and Smoke Protection Features, Through-Penetration Firestop System
, with a minimum positive pressure differential of 0.01 inch (2.49 Pa) of water and shall have an F rating of not less than the required fire ...
Building Code 2018 of Kansas > 7 Fire and Smoke Protection Features > 714 Penetrations > 714.4 Fire-Resistance-Rated Walls > 714.4.1 Through Penetrations > 7126.96.36.199 Through-Penetration Firestop System