// CODE SNIPPET
43.6.4 Extinguishing Systems
JUMP TO FULL CODE CHAPTER
In a building with rehabilitation work areas involving over 50 percent of the aggregate building area, automatic sprinkler systems shall be provided on the highest floor containing a rehabilitation work area and on all floors below in accordance with the requirements of other sections of this Code applicable to new construction for the occupancy.
Where sprinklers are installed in an elevator hoistway or elevator machine room as part of the rehabilitation work, the elevators shall comply with the fire fighters' emergency operations requirements of ASME A17.1/CSA B44, Safety Code for Elevators and Escalators.
The standpipes required by 126.96.36.199 shall be located and installed in accordance with NFPA 14 unless otherwise provided in 188.8.131.52 and 184.108.40.206.
No pump shall be required, provided that the following criteria are met:
- The standpipes are capable of accepting delivery by fire department apparatus of a minimum of 250 gpm at 65 psi (945 L/min at 4.5 bar) to the topmost floor in buildings equipped throughout with an automatic sprinkler system or a minimum of 500 gpm at 65 psi (1890 L/min at 4.5 bar) to the topmost floor in other buildings.
- Where the standpipe terminates below the topmost floor, the standpipe is designed to meet the flow/pressure requirements of 220.127.116.11(1) for possible future extension of the standpipe.
Related Code Sections
43.6.4 Building Rehabilitation, Extinguishing Systems
In a building with rehabilitation work areas involving over 50 percent of the aggregate building area, automatic sprinkler systems shall be provided ...
Life Safety Code 2018 of Kansas > 43 Building Rehabilitation > 43.6 Reconstruction > 43.6.4 Extinguishing Systems
118.104.22.168 Energy Systems, Fire-Extinguishing Systems
battery types are not addressed in Chapter 5 of NFPA 13, the fire code official is authorized to approve the fire-extinguishing system based on full-scale ...
Fire Code 2018 of Kansas > 12 Energy Systems > 1206 Electrical Energy Storage Systems > 1206.2 Stationary Storage Battery Systems > 1206.2.11 Fire-Extinguishing and Detection Systems > 122.214.171.124 Fire-Extinguishing Systems
2309.3.1.5.2 Motor Fuel-Dispensing Facilities and Repair Garages, Fire-Extinguishing Systems
Fuel-dispensing areas under canopies shall be equipped throughout with an approved automatic sprinkler system in accordance with Section 903.3.1.1 ...
Fire Code 2018 of Kansas > 23 Motor Fuel-Dispensing Facilities and Repair Garages > 2309 Hydrogen Motor Fuel-Dispensing and Generation Facilities > 2309.3 Location on Property > 2309.3.1 Location of Operations and Equipment > 2309.3.1.5 Canopy Tops > 2309.3.1.5.2 Fire-Extinguishing Systems
2405.4.1.1 Flammable Finishes, Fire-Extinguishing System
An approved automatic fire-extinguishing system shall be provided for dip tanks with a 150-gallon (568 L) or more capacity or 10 square feet ...
Fire Code 2018 of Kansas > 24 Flammable Finishes > 2405 Dipping Operations > 2405.4 Fire Protection > 2405.4.1 Fixed Fire-Extinguishing Equipment > 2405.4.1.1 Fire-Extinguishing System
126.96.36.199 New Mercantile Occupancies, Automatic Extinguishing Systems
The mall structure and all anchor buildings shall be protected throughout by an approved, supervised automatic sprinkler system in accordance ...
Life Safety Code 2018 of Kansas > 36 New Mercantile Occupancies > 36.4 Special Provisions > 36.4.4* Mall Structures > 188.8.131.52 Automatic Extinguishing Systems