// CODE SNIPPET
2111.14.3 Exterior Air Intake
JUMP TO FULL CODE CHAPTER
The exterior air intake shall be capable of providing all combustion air from the exterior of the dwelling. The exterior air intake shall not be located within a garage, attic, basement or crawl space of the dwelling nor shall the air intake be located at an elevation higher than the firebox. The exterior air intake shall be covered with a corrosion-resistant screen of 1/4-inch (6.4 mm) mesh.
Related Code Sections
2111.14.3 Masonry, Exterior Air Intake
The exterior air intake shall be capable of providing all combustion air from the exterior of the dwelling . The exterior air intake shall ...
Building Code 2018 of Illinois > 21 Masonry > 2111 Masonry Fireplaces > 2111.14 Exterior Air > 2111.14.3 Exterior Air Intake
1205.3.2 Interior Environment, Air Intake
Courts more than two stories in height shall be provided with a horizontal air intake at the bottom not less than 10 square feet (0.93 m 2 ...
Building Code 2018 of Illinois > 12 Interior Environment > 1205 Yards or Courts > 1205.3 Courts > 1205.3.2 Air Intake
1024.7 Means of Egress, Ventilation
as required for shafts. Where the equipment and ductwork is located within the exit passageway, the intake air shall be taken directly from the outdoors ...
1023.6 Means of Egress, Ventilation
, the intake air shall be taken directly from the outdoors and the exhaust air shall be discharged directly to the outdoors, or such air shall ...
Building Code 2018 of Illinois > 10 Means of Egress > 1023 Interior Exit Stairways and Ramps > 1023.6 Ventilation
R402.4 [RE] Residential Energy Efficiency, Air Leakage (Mandatory)
General requirements A continuous air barrier shall be installed in the building envelope. The exterior thermal envelope contains a continuous air ...
2018 Illinois Energy Conservation Code Standards for Privately Funded Commercial Facilities and Standards for Residential Buildings > 4 [RE] Residential Energy Efficiency > R402 Building Thermal Envelope > R402.4 Air Leakage (Mandatory)