// CODE SNIPPET
(6) 604.6 Exit and Emergency Lighting Equipment
JUMP TO FULL CODE CHAPTER
An activation test of the exit and emergency lighting equipment with self contained battery back-up power shall be performed monthly for a period of not less than 30 seconds.
To insure continued illumination for a duration of not less than 90 minutes as listed in paragraph (K)(5)(c)(1011.5.3) of rule 1301:7-7-10 of the Administrative Code, exit and emergency lights equipped with self contained battery back-up power shall be tested annually for a period of not less than 90 minutes.
A written record of all inspection, testing and maintenance of exit and emergency lighting equipment shall be documented and available for review by the fire code official.
Related Code Sections
604.6 Ohio Administrative Code 1301:7-7-06 Building Services and Systems, Exit and Emergency Lighting Equipment
Exit and emergency lighting equipment with self contained battery back-up power shall be inspected and tested in accordance with paragraphs (D)(6 ...
Ohio Fire Code 2011 > Ohio Administrative Code 1301:7-7-06 Building Services and Systems > 604 Emergency and Standby Power Systems > 604.6 Exit and Emergency Lighting Equipment
646.16 Special Equipment, Emergency Lighting
Areas that are used for exit access and exit discharge shall be provided with emergency lighting. Emergency lighting systems shall be listed ...
National Electrical Code 2017 of Ohio > 6 Special Equipment > 646 Modular Data Centers > 646.16 Emergency Lighting
1008.3 Means of Egress, Emergency Power for Illumination
of egress, an emergency electrical system shall automatically illuminate all of the following areas: Aisles . Corridors . Exit access ...
Ohio Building Code 2017 > 10 Means of Egress > 1008 Means of Egress Illumination > 1008.3 Emergency Power for Illumination
(F) Special Conditions, Unit Equipment
Individual unit equipment for emergency illumination shall consist of the following: A rechargeable battery A battery charging means ...
National Electrical Code 2017 of Ohio > 7 Special Conditions > 700 Emergency Systems > 700.12 General Requirements > (F) Unit Equipment
405.8 Special Detailed Requirements Based on Use and Occupancy, Standby and Emergency Power
loads: Emergency voice/alarm communications systems . Fire alarm systems. Automatic fire detection systems. Elevator car lighting ...
Ohio Building Code 2017 > 4 Special Detailed Requirements Based on Use and Occupancy > 405 Underground Buildings > 405.8 Standby and Emergency Power