// CODE SNIPPET
601.3 Existing Piping Used for Grounding
Related Code Sections
601.3 Water Supply and Distribution, Existing Piping Used for Grounding
Existing metallic water service piping used for electrical grounding shall not be replaced with nonmetallic pipe or tubing until other approved ...
Plumbing Code 2018 of Kansas > 6 Water Supply and Distribution > 601 General > 601.3 Existing Piping Used for Grounding
(D) Wiring and Protection, Separately Derived Systems
piping system is used as the grounding electrode for the separately derived system and the water piping system is in the area served. Exception No. 2: A ...
National Electrical Code 2017 of Kansas > 2 Wiring and Protection > 250 Grounding and Bonding > 250.104 Bonding of Piping Systems and Exposed Structural Metal > (D) Separately Derived Systems
5703.6.3.1 Flammable and Combustible Liquids, Existing Piping
Existing piping shall be tested in accordance with this section where the fire code official has reasonable cause to believe that a leak exists ...
Fire Code 2018 of Kansas > 57 Flammable and Combustible Liquids > 5703 General Requirements > 5703.6 Piping Systems > 5703.6.3 Testing > 5703.6.3.1 Existing Piping
309.1 General Regulations, Grounding
Gas piping shall not be used as a grounding electrode ...