// CODE SNIPPET
804.3.7 Exhauster Sizing
Related Code Sections
804.3.7 Chimneys and Vents, Exhauster Sizing
Mechanical flue exhausters and the vent system served shall be sized and installed in accordance with the manufacturer's installation instructions ...
Mechanical Code 2018 of Maryland > 8 Chimneys and Vents > 804 Direct-Vent, Integral Vent and Mechanical Draft Systems > 804.3 Mechanical Draft Systems > 804.3.7 Exhauster Sizing
504.8.1 Exhaust Systems, Material and Size
Exhaust ducts shall have a smooth interior finish and shall be constructed of metal not less than 0.016 inch (0.4 mm) in thickness. The exhaust duct ...
Mechanical Code 2018 of Maryland > 5 Exhaust Systems > 504 Clothes Dryer Exhaust > 504.8 Domestic Clothes Dryer Ducts > 504.8.1 Material and Size
507.4.1 Exhaust Systems, Canopy Size and Location
The inside lower edge of canopy-type Type I and II commercial hoods shall overhang or extend a horizontal distance of not less than 6 inches (152 mm ...
Mechanical Code 2018 of Maryland > 5 Exhaust Systems > 507 Commercial Kitchen Hoods > 507.4 Hood Size and Location > 507.4.1 Canopy Size and Location